HOME › Forums › Forums › Fire Code & Enforcement › Visual AND audible device attached to kitchen system › Reply To: Visual AND audible device attached to kitchen system
It’s in NFPA 96.
10.6 System Annunciation.
10.6.1 Upon activation of an automatic fire-extinguishing system,
an audible alarm or visual indicator shall be provided to
show that the system has activated.
A bell can be added for audible and most systems agent canisters have a visual indicator on them showing the extinguishing agent has been discharged.
Hope this helps.