- Department Name: Perth Fire Services
Thanks for pointing out the OBC vs S524 difference for the installation of the components.
The sprinkler system requires annunciation on the fire alarm panel but since a fire alarm system is not required, how do you have a fire alarm panel without a fire alarm system? Yes, it’s very convoluted.
It’s not the Architect saying the fire alarm system is required. It’s the CBO and myself. The Architect is proposing to supervise the sprinkler system components and annunciate & transmit notification to the FD with something other than a true fire alarm panel. What that ‘something’ is, we have no idea, nor to what standards its installed to (but it has to meet S561 for the transmission part) and also no information on maintenance standards.
I think they’ve spent more time and effort trying to figure out a way to not install a dozen or so pull stations and a couple extra smokes than it would have taken to just install them and be done with it.